Greer’s Service Company provides personal, reliable, high quality air conditioning and heating services to the residents of Cary, NC. From new installation to maintenance and repair, we can resolve any issue your home comfort system has!
We’ve served the Cary, NC area for over 40 years. Check out our excellent reviews to see how we can help you today!
for Cary, NC
Our Reviews by City
Vicki - Cary, NC
Thanks for keeping us up and running!!
Excellent, honest family business.
Ralph - Cary, NC
None of the big service names had any interest in repairing my older equipment, they just pushed expensive new replacements. I wasn't ready to upgrade, and fortunately my neighbor recommended that I call Greer. They kept my aging units going until there was more rust than metal, and finally I gave in and had them put in fancy new units at a fair price. I am very happy with the result and as claimed, they work better and use less electricity. Today my installation team came back out for our spring tune-up and it was like a reunion of old friends. I genuinely like these guys and if you enjoy doing business with competent, honest local folks who care, you will too.
Zane - Cary, NC
Very proffesional, great job
David j G.
Preformed maintenance on a 2010 Trane duel fuel Trane package unit. Tightened wires took amps, checked evaporator coil it was clean. Then checked the furnace side of it and cleared pressure switch, checked safeties, checked flame rod and hot surface igniter all working in manufacturers specifications.
David j G.
Preformed maintenance on a Goodman straight AC. Cleaned outdoor coil, cleared drain, tightened wires, checked refrigerant everything was running like it’s supposed to.
Conducted 2 spring tune ups for a Rheem A/C and a Trane A/C system. Cleaned 2 condenser coils and added 1.5 lbs Puron (R-410a) refrigerant to each and cleared the drain lines.
David j G.
Preformed 2 maintenance’s on 4 year old Carrier units one is a heat pump and the other is a straight AC. Cleaned both coils and cleared drains and tightened wires and checked refrigerant everything was running like it’s supposed to.
Adjustment on TXV. Let some puron out. Had to clean copper and sensor bulb with sandpaper because of corrosion on both, so bulb sending false readings
Heat pump repair. Diagnose and perform annual heating maintenance on Amana Heating System. Inspect heat exchanger for deterioration. Check fan switch. Clean and adjust pilot assembly on 10 year old HVAC system. Replace air filters. Furnace maintenance complete which will help lower heating cost for residential customer. Furnace system is now ready for the winter weather.